In the Johnson County Kansas, Ideal Air Heating and Cooling is well known for providing exceptional repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Ideal Air Heating and Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Heat Pump, & Furnace Repair in Spring Hill, KS in Olathe KS. Call us today at 913.422.7373!
The entire Ideal Air team is professional and provides service you can trust. Thank you!
Perform furnace tune up on 2016 York system. PM check on electrical and ignition systems, safety controls, flame sensor, service and test of humidifier. Also check filter and dampers. Clean system.
Performed AC tune up on 2013 York heat pump. PM check on electrical, refrigerant pressures, filter, air flow and performance of system. Adjusted dampers and turned off humidifier.
I replaced a leaking evaporator coil.
Performed furnace tune up on 2015 York Air Handler and Heat Pump. PM check on electrical and ignition systems, safety controls, service and test of humidifier. Also checked 20x25x1 filter and dampers.
Perform complete A/C tune up. Clean outdoor unit. Check all electrical both at air conditioner and at the furnace. Check motors. Check refrigerant charge for proper pressures and temperatures.
Performed tune up on 2014 York heat pump. Checked electrical wiring and connections. Checked filter and left replacements. Tested motors and capacitors. Tested refrigerant temperatures and pressures.
Performed a air conditioner check out on Goodman system. I checked Freon and electrical amps.
General 900 humidifier service with water pad replacement. York furnace tune up
Annual Goodman furnace tune up
York air conditioner seasonal tune up. Plus cleared condensate drain
Air conditioner tune up. Also found the system short of Freon; recharged system up to proper pressures and replaced the primary motor starter.
Replace blower motor on indoor section.
Responded to a non-working Goodman system. Replaced the standard capacitor with a heavy duty turbo capacitor and recharged the system up to proper pressures with R410A Freon.
Diagnosed a non-working York air conditioner. Installed a compressor saver matched to the compressor.
Seasonal AC tune up on a Goodman air conditioner. Turned off humidifier which does have a water valve stuck in the on position. Should fix at fall furnace tune up.
Removed old Lennox air conditioner and coil. Installed New York air conditioner and coil. Vacuumed the system and charged to proper temperature and pressures.