In the Johnson County Kansas, Ideal Air Heating and Cooling is well known for providing exceptional furnace repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Ideal Air Heating and Cooling because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Heat Pump, & Furnace Repair in Mission, KS in Olathe KS. Call us today at 913.422.7373!
Punctual, polite, get it done attitude!
A/C stopped working and Sterling was able to identify the problem and quickly fixed.
Installed a New Water Heater
Installed a 20 seer Amana system
Installed a new Furnace, Air Conditioner, and Evaporator coil.
Perform AC tune up on 2017 Amana. PM check on electrical, freon pressures, filter, air flow and performance of system. Check dampers and turn off humidifier. Clean AC.
Perform ac tune up on Lennox air conditioner.
I replaced a leaking evaporator coil with a new one. I pressure tested the refrigeration system, ran a deep vacuum and charged it to proper pressures.
I serviced a York system.
Perofrmed ac tune up on a York air conditioner.
I replaced a limit switch on a York furnace.
Replaced the primary limit switch on a York furnace.
Replaced a Rheem inducer motor on a Furnace.
Performed furnace tune up on 2008 Lennox. PM check on electrical and ignition systems, safety controls, flame sensor, service and test of humidifier. Also checked Expansion filter and dampers.
Checked furnace operation. Checked furnace blower and all electrical. Removed, cleaned, and tested ignition system. Checked all safety components. Check gas iinputs and temperatures. Test sequence of operation.
Performed a Furnace check up on a York furnace. I vacuumed it out, I checked the temperature rise, I checked safety switches, and I replaced the 20x25x5 air bear filter.
Diagnose faulty wireless thermostat and a leaking evaporator coil.
Began maintenance plan and furnace tune up.
Lennox furnace tune up Aprilaire humidifier service and water pad replacement.
Annual Amana furnace tune up
Annual Rheem furnace tune up
Air conditioner tune up on a Kenmore system. Also replaced the blower motor and a primary motor starter in the outdoor unit.
Performed a comprehensive seasonal tune up and maintenance check on York air conditioner.
Performed tune up on 2003 Lennox air-conditioner. Found failed to contact her and replaced. Locate and repair short caused by a mouse chewing through wiring. Test equipment operation. Test R22 refrigerant temperatures and pressures. Washed condensing unit.
Performed an air conditioning tuneup on a Heil air conditioner. Washed the outdoor unit. Checked all electrical components. Checked the filter and thermostat. Verified proper Freon pressures, sub cooling, and temperature drop,
Performed repair on 2000 carrier air conditioner. Replaced dual voltage absorber. Performed air conditioner super tuneup. Tested equipment operation.