Since 2006, Ideal Air Heating and Cooling is your best choice for repair, installation, and service in homes and buildings just like yours in the Johnson County Kansas. We take special pride in the craftsmen we train and employ--a fact you'll see in the reviews below. It's also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Ideal Air Heating and Cooling stands behind the work we do as well as complies with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC, Heat Pump, & Furnace Repair in Kansas City, KS. Call us today at 913.422.7373!
Worked efficiently to get my furnace working again with no attempts at upselling ( I hate that! )
Service was prompt and the issue was fixed.
Started a new Amana Air Conditioner
We installed (2) two stage furnaces
Installed two EAC filters and UV Lamps
I serviced a York furnace and replaced a bad circuit board.
Performed Furnace check out on a York furnace. I checked safety switches and electrical components.
Performed a/c check out
Performed air conditioner checkout on a York
Performed air conditioner tune up on a York system
Annual York furnace tune up
Annual York furnace tune up. Air Bear filter replacement
Annual American Standard furnace tune up
Annual York furnace maintenance/service/tune up
York furnace tune up
Replace thermostat for a York air conditioner.
Performed annual air conditioner maintenance on a York air conditioner. replaced air bear filter
Performed annual air conditioner maintenance on an American Standard air conditioner.
Performed seasonal comprehensive tune up and maintenance check on a York air conditioner.
Perform tuneup on 2010 York air-conditioner. Checked electrical wiring and connections. Checked R410a refrigerant temperatures and pressures. Check and replace air bear filter. Test equipment operation. Washed condensing coil.
Performed tune up on 2007 American Standard air conditioner. Checked electrical wiring and components. Check and replace Air Bear filter. Test R 410 a refrigerant temperatures and pressures. Test air-conditioner operation. Wash outside condensing unit.
Responded to a no heat call on a Tempstar furnace. Found the cause of the problem was a bad Smart gas valve. Replaced the valve to correct and checked operation. Checked all of the safety controls. Check the firing rate and temperature rise.
Performed repair on 2008 Lennox air conditioner. Replaced failed contactor and washed outside unit. Tested unit operation.