The general principle on which most air conditioners in Olathe work is this: they contain a chemical that easily transforms from a gas to a liquid and back again. This chemical removes heat from the air inside the room and transfers it to the air outside, thus cooling the inside of an Olathe room or a building. Heat pumps are a special sort of AC that operates slightly differently.
A heat pump contains a valve that allows it to switch function, depending on the need. The pump functions as an Olathe furnace when the valve is switched in a particular direction. When the valve is switched in the other direction it functions as an AC.
for Olathe, KS
Melody - Olathe, KS
Richard was wonderful! We would not hesitate to call on them again!
Great service, Superior Tech
Cliff - Olathe, KS
Knowledgeable and polite
Kayla - Olathe, KS
The service tech that came to our house was very thorough and pleasant. He explained to me a few things we could do on our end to help our heating costs and explained in very easy terms what we needed without pressuring to buy. I did buy the package for having them service the furnace in the fall, but never felt pressured to do so. Just felt he knew what he was about and wasn't trying to get extra money out of us.
Furnace blower repair
Regina - Olathe, KS
Great service, prompt, reasonable. Repaired in a short time. Thanks for the quick response. Richard repaired air conditioning earlier in the year and did a great job then, too!
Clark - Olathe, KS
Great service, went above and beyond addressing the issue and then some!
Mike - Olathe, KS
Sterling seems to really know what he’s doing. He seemed honest and truly concerned with the air conditioner’s functionality. I was a bit shocked at the price, in particular, the trip fee. That fee seems like a “pile-on” fee that takes advantage of the situation. I’ve had other heating and air companies to the house for repairs, and I was never charged a trip fee (it was probably built-in; but it was not apparent). I was not aware of the trip fee until the work was complete and the invoice was being written up.
Always a Great Experience
Libbie - Olathe, KS
Ideal Air is a thoroughly professional company with fast response times, highly competent technicians and all-around friendly staff!
Nick - Olathe, KS
Service techs were great, very helpful
Lisa - Olathe, KS
proffessional and friendly
Seth - Olathe, KS
Richard is always very good to work with.
Diana - Olathe, KS
Great Service, Always
Renee - Olathe, KS
Honest folks, and extremely courteous and friendly.
Elaine - Olathe, KS
Great service, reasonable price.
Mark - Olathe, KS
Great service, reasonable price. They act like they want you as a repeat customer, not all they can get on every call. Have never had an issue, but when small problems pop up they are always fixed to our satisfaction.
Fantastic service & price!
Kristy - Olathe, KS
I was excited that Richard was able to come out right away. Then he fixed the problem with my furnace very quickly and reasonably.
Performed repair on 2005 carrier air-conditioner. Replaced secondary motor controller. Tested R 22 refrigerant charge. Tested equipment operation.
Performed repair on 1999 Lennox air conditioner. Replaced failed dual voltage absorber. Reset high pressure limit switch. Tested equipment operation.set dampers to cooling positions and turned off humidifier
Performed repair on 2005 Carrier air conditioner. Replaced voltage distributor/contactor. Tested unit operation. Tested R22 refrigerant temperatures and pressures. Tested temperature drops. Washed outside coil.
Performed repair on 2005 carrier air conditioner. Replaced secondary motor controller. Tested equipment operation.
Serviced and repaired on a 2005 Lennox air conditioner. The cause of problem was a failed duel capacitor replaced and tested a/c
Performed a service call on a Lennox air conditioner. The r22 pressures were equalized. Check for amps and had 0 Amps. Checked the capacitor and had 0 µF. Replaced capacitor and had normal operation. Checked refrigerant levels and temperature drop.
Performed an air conditioner tuneup on a Lennox air conditioner. Checked all the electrical system. Replaced the filter. Washed the outdoor unit. Checked the Freon charge. Adjusted they R-22 charge to bring proper pressures and temperatures.
Had a no air conditioning call in Olathe on an American Standard air conditioner. Found the cause of the problem was a bad capacitor. Replaced the capacitor to correct. Checked system operation. Checked Freon levels. Checked for proper levels of R-22 and for proper temperatures and pressures.
Had an AC repair on a York air conditioner. It was not running. Checked it and found it had a bad contactor and a bad capacitor. Replaced both and checked operation. Checked Freon levels. Added R 22 to bring to proper pressures and temperatures.
Performed a service call for a air-conditioner that was not working. Checked temperature drops on the indoor coil. Went outside and checked the refrigerant levels and pressures. Noticed it was low added 27 ounces of r410-a refrigerant. Temperatures and pressures were correct after adding the refrigerant and had a 21° temperature drop
Serviced and repaired a 1999 Lennox air conditioner found out that it was low on refrigerant. Charged it back to its proper pressures and temperatures
Performed seasonal tuneup on a 2001 temp star air conditioner. Air-conditioner was low on refrigerantcharged it back to proper temperatures and pressures
Performed a repair on a 1995 Lennox air conditioner The cause of problem was that the air conditioner was low on refrigerant. Charged it to its proper pressures and temperatures. And also check the temperature drop and temperature rise
Performed an AC repair on a Lennox air conditioner. Checked the system operation. Checked the White Rodgers thermostat. Turned off the Aprilaire humidifier. Set the dampers for summer. Checked all of the electrical connections. Checked the capacitor. System was short of Freon. Recharged the system with R-22. Verified proper pressures and temperatures.
Performed a spring air conditioner tuneup on a York system. Checked the thermostat. Checked the Air Bear filter and the humidifier. Checked all of the electrical connections. Checked the refrigerant charge. Verified proper pressures of R-410a Freon.
Performed an air-conditioner tuneup on a Lennox air-conditioner. Checked operation of the system. Turned off the humidifier. Checked the air bear filter. Checked the blower wheel and blower motor on the furnace. Completely checked the outdoor unit. Checked all of the electrical components. Checked the refrigerant charge. Verified proper Freon levels of R-22.
Performed the spring air conditioner maintenance check on a Carrier air conditioner. Washed the outdoor unit. Replaced the furnace filter. Checked the contactor, capacitor, and fan motor, and checked all electrical connections. Checked refrigerant charge. Verified proper R-22 Freon pressures and temperatures.
Performed a spring air conditioner tuneup on a Rheem air-conditioning system. Washed the system. Checked all of the electrical components. Checked the R-22 freon charge. Checked the temperature drops and pressures. Customer elected to purchase a maintenance program at this time.
Removed the old Lennox furnace and air conditioner. Replaced with a new high efficiency 95% furnace and air conditioner.
Responded to a no heat call on a Lennox furnace. Checked the furnace and found it had a failed primary control board. Replaced the main control board and checked the furnace operation. Checked all the electrical components. Checked the gas pressure, the gas input, and the temperature rise.
Responded to a no heat call on a Trane furnace. Found that the main primary circuit board was bad. Replaced the board to correct the problem and checked the operation. Checked all of the furnace operation. Checked all of the safety controls. Checked the flame and flame sensor. Checked the gas pressure and temperature rise.
I responded to a no heat call on a Coleman furnace. Checked the furnace operation and found it had a bad furnace control relay. Replaced the relay to correct and checked furnace operation. Checked all electrical. Checked gas cycling and temperature rise.