Average Americans in Lenexa spend nearly 90% of their time indoors. For the infants, the elderly and the urban residents, in Lenexa this percent of time is likely to be higher. Studies show that indoor air pollution can be two to five times to sometimes 100 times higher than outdoor air pollution.
This puts the citizens in Lenexa to a greater risk of contracting various diseases from Lenexa indoor air pollutants. In fact, the US Environmental Protection Agency, EPA ranks poor indoor air quality one among the top five public health risks. Common diseases and symptoms are associated with poor indoor air quality.
for Lenexa, KS
Always great service!
Kim - Lenexa, KS
We love Ideal Air because of the wonderful customer service!!
Amy - Lenexa, KS
Patricia - Lenexa, KS
Was really happy came out same day
Matt - Lenexa, KS
I have been working with Ideal Air for 9+ years. I've recommended them to several family and friends for their terrific service, pricing and loyalty.
Richard - Lenexa, KS
Kristen - Lenexa, KS
Fast service, came as soon as we needed them, fixed problem right away.
Excellent and professional service.
Cliff - Lenexa, KS
Excellent service by two professionals...Sterling and Jose.
Nelson - Lenexa, KS
Professional and thorough. Explained our options for a new unit very well. Prices very competitive.
Jim - Lenexa, KS
Always great service. Care about customer and customers' concerns
Nancy - Lenexa, KS
I am always pleased with timeliness, the friendliness, and promptness of service individuals I deal with.
Performed seasonal comprehensive tune up and maintenance check on a Amana system.
Performed a comprehensive seasonal tune up and maintenance check on Goodman system.
Performed seasonal spring tune up's on two Lennox systems.
American Standard heat pump not working. Replaced capacitor and also performed spring tune up on an American Standard air conditioner.
Performed repair on 2008 Arcoaire air conditioner. Recharge system to correct temperatures and pressures of our 22 Freon. Performed tune up on outside condensing unit. Test electrical components connections and operation. Test temperature rise and indoor temperature drop. Check filter. Wash outside condensing coil.
No Cooling on a Lennox air-conditioner. The condensor fan motor is bad. Replace the motor to correct and check operation. Wash the outdoor unit. Complete AC tuneup. System is a little short of Freon. Charge to proper R-22 pressures and temperatures.
Customer has no A/C on a Carrier air conditioner. System needs an air-conditioner tuneup, plus, it is short of Freon. Perform full AC tuneup. Check the system operation. Charge the system to proper R-22 temperatures and pressures.
Perform spring air-conditioner tuneup. The pressures are very low and temperatures also are very low. That indicates poor airflow or a restricted evaporator coil. Fan capacitor is bad and filters are very dirty. Replace both and recheck the system. Check the Freon charge. Check for R22 pressures and temperatures. The repair made very little difference in operation. The furnace and air conditioner need to be replaced.
Perform spring maintenance air-conditioner tuneup. Turn off the Aprilaire humidifier. Replace the Air Bear filter. Check the Ecobee thermostat. Check the furnace blower motor. Wash the York condenser unit. Check the capacitor and contactor. Check the Freon levels. Verify proper R410 a pressures and temperatures.
Perform a spring A/C tuneup on a Trane air conditioner. Check thermostat. Replace air filter. Adjust dampers. Check the furnace blower motor. Wash the condenser coil. Check all electrical. Check the Freon charge. Verify proper R-22 pressures and temperatures.
Installed new Amana equipment
Performed tune up on 2008 Ideal Air air conditioner. Check electrical wiring and connections. Test R410a Freon refrigerant temperatures and pressures. Check filter. Turn off humidifier. Test air-conditioner operation. Wash outside condensing unit.
Air-conditioner not cooling, 2010 Nordyne unit. Found system needed a new dual voltage absorber. Replaced and tested equipment. Found unit was running low on R22 refrigerant. Added refrigerant to bring temperatures and pressures to correct levels. Also added leak sealant to prevent further Freon leaks. Performed tune up on system. Tested electrical wiring and connections. Checked filter. Tested equipment operation. Washed condensing unit.
Perform tuneup on carrier air conditioner. AC was low on Freon charged it back up to its proper pressures and temperatures. Also Checked all the electrical.
Performed Tune up on Lennox air conditioner, checked freon levels and electrical wiring. Checked air filter and air dampers.
Responded to a no air conditioning call. Arrived at the home and found that the system was iced up. Checked all the electrical. Checked the blower motor and capacitor. Thawed out the system. Started and ran the unit. Found the freon charge to be low. Charged with R410a to proper pressures and temperatures.
Performed tune up on 2012 train air conditioner. Tested electrical components and connections. Tested refrigerant R410a pressures and temperatures. Check filter. Checked airflow through house. Set fan to circulate air flow.
Performed tuneup and repair on 2004 Lennox air conditioner. Replaced secondary motor controller. Tested all electrical components and connections. Tested refrigerant r22 Freon temperatures and pressures. Tested equipment operation. Washed outside condenser coil.
Performed AC tuneup on 2002 Lenix air conditioner. Tested refrigerant pressures and temperatures. Tested electrical components. Tested airflow and temperature drops.washed outside condenser
Performed a service call on a Lennox air conditioner. The capacitor was below manufacturer specs and would not run fan motor.I replaced the capacitor and reset the pressure switch and it began to run. Checked the pressures of R 22 which ran perfect according to temperature.