Average Americans in Lenexa spend nearly 90% of their time indoors. For the infants, the elderly and the urban residents, in Lenexa this percent of time is likely to be higher. Studies show that indoor air pollution can be two to five times to sometimes 100 times higher than outdoor air pollution.
This puts the citizens in Lenexa to a greater risk of contracting various diseases from Lenexa indoor air pollutants. In fact, the US Environmental Protection Agency, EPA ranks poor indoor air quality one among the top five public health risks. Common diseases and symptoms are associated with poor indoor air quality.
for Lenexa, KS
Matt - Lenexa, KS
I have been working with Ideal Air for 9+ years. I've recommended them to several family and friends for their terrific service, pricing and loyalty.
Richard - Lenexa, KS
Kristen - Lenexa, KS
Fast service, came as soon as we needed them, fixed problem right away.
Excellent and professional service.
Cliff - Lenexa, KS
Excellent service by two professionals...Sterling and Jose.
Nelson - Lenexa, KS
Professional and thorough. Explained our options for a new unit very well. Prices very competitive.
Jim - Lenexa, KS
Always great service. Care about customer and customers' concerns
Nancy - Lenexa, KS
I am always pleased with timeliness, the friendliness, and promptness of service individuals I deal with.
Pam - Lenexa, KS
Excellent professional service!
Cliff - Lenexa, KS
Richard always does excellent service here. He always explains exactly what he is doing...no surprises.
Responded to a no air conditioning call. Arrived at the home and found that the system was iced up. Checked all the electrical. Checked the blower motor and capacitor. Thawed out the system. Started and ran the unit. Found the freon charge to be low. Charged with R410a to proper pressures and temperatures.
Performed tune up on 2012 train air conditioner. Tested electrical components and connections. Tested refrigerant R410a pressures and temperatures. Check filter. Checked airflow through house. Set fan to circulate air flow.
Performed tuneup and repair on 2004 Lennox air conditioner. Replaced secondary motor controller. Tested all electrical components and connections. Tested refrigerant r22 Freon temperatures and pressures. Tested equipment operation. Washed outside condenser coil.
Performed AC tuneup on 2002 Lenix air conditioner. Tested refrigerant pressures and temperatures. Tested electrical components. Tested airflow and temperature drops.washed outside condenser
Performed a service call on a Lennox air conditioner. The capacitor was below manufacturer specs and would not run fan motor.I replaced the capacitor and reset the pressure switch and it began to run. Checked the pressures of R 22 which ran perfect according to temperature.
Performed seasonal tune up on York air conditioner
Performed an air-conditioner tuneup on a Lennox air conditioner. Checked the furnace and all electrical connections. Checked the furnace filter. Washed the outdoor unit. Checked all of the electrical in the outdoor unit. Checked the Freon charge. Verified proper pressures and temperatures. Installed a new Sensi wi-fi thermostat.
Had no heat on an American Standard variable speed furnace. Found the cause of the problem was a bad variable speed control module. Replaced the module to correct and checked the furnace operation.
Performed a furnace tuneup on a Lennox furnace. Checked filter checked humidifier and water pad checked for temperature rise checked dampers and tested capacitor. Also fixed a damper that was loose in the ceiling and making a rattling noise.
Performed service and repair on Coleman furnace and air conditioner. Found failed control board and voltage absorber in furnace causing blower to not operate correctly. Replaced failed components and tested equipment operation.
Had a no cooling call in Lenexa on a Lennox air conditioner. Found cause of the problem to be a bad outdoor fan motor and a bad capacitor. Replaced both to correct and checked operation. Washed the outdoor unit. Checked R-22 Freon levels in the system. Verified proper pressures and temperatures.
Installed new York air conditioner and furnace. Install general 900 humidifier. Tested equipment operation.
Performed diagnostic. Found failed blower motor. Removed and replaced motor. Tested equipment operation.
Performed tune up on 2004 Lennox furnace and air conditioner. Tested refrigerant temperatures and pressures. Checked electrical components. Washed outside condenser. Checked filter. Tested furnace safety controls. Checked electrical wiring and controls. Checked furnace control board. Tested temperature rise/drop. Serviced humidifier. Cleared humidifier water line and tested operation.
Removed and replaced TXV. Pulled the vacuum to test for leaks. Added refrigerant dye kit to be able to find potential leaks in the future. Charge system to correct temperatures and pressures.
Performed repair on 2002 Linick's air conditioner. Replaced the capacitor. Added 19 ounces of our r22 Freon. tested equipment operation.
Installed new York furnace and air conditioner, installed air bear filter system, installed general air humidifier for the whole house. Tested equipment.
Installed new 90% York furnace and high efficiency air conditioner. Installed Air Bear filter and Whole house humidifier. Tested system operation.
Performed an air-conditioner tuneup on a Lennox model 10 ACC-048–230-02. Checked the thermostat. Replaced the filter. Adjusted the dampers. Checked the condensate drain. Washed the outdoor unit. Checked and tightened all electrical connections. Checked the Freon charge. Added 39 ounces of R-22 to bring to proper pressures and temperatures.