When you are choosing for the right air conditioning unit in Gardner, you will find some useful information for comparing different units right online. This helps you do a side-by-side comparison instead of running from store to store. You will not only save time, but you will even find some brands of air conditioners that are not found in your area.
As Gardner home air conditioning units process the warm air within a home, they also cool the air by moving the air through a refrigerant coil filled with gas (Freon). This process also takes away a good part of the humidity that was present in the home, especially on hot, summer days. This circulation provides cleaner and healthier air, resulting in a better living environment for you and your family. Having a proper home air conditioning unit in your home will ensure that your family’s air stays clean and healthy while they are enjoying all those indoor family activities. Your Gardner home also benefits from being free of the high humility’s and hot temperatures.
for Gardner, KS
Great customer service. Friendly & knowledgeable staff!!!
Chad - Gardner, KS
Great support & lots of patience to satisfy customers questions/concerns. The attention to detail is amazing as well.
Performed tuneup on 1998 Lennox air conditioner. Tested electrical wiring and components. Tested refrigerant R22 temperatures and pressures. Tested temperature drop inside the house. Washed outside condenser. Added R22 Freon to bring temperatures and pressures to correct levels.
Performed tune up on 2006 Lennox air-conditioner. Tested electrical components and connections. Tested refrigerant temperatures and pressures. Added our 22 Freon to bring pressures to correct levels. Tested equipment operation. Washed outside condenser unit.
Had an air conditioning problem in Gardner Kansas on a Trane air conditioner. Found the cause of the problem was a failed furnace main circuit board. Replaced the board to correct and checked the operation. Checked all of the electrical and found a bad furnace blower capacitor. Installed a new capacitor to correct. Checked the air conditioner operation. Washed the outdoor unit. Checked Freon levels. Added 8 ounces of R-22 Freon to bring to proper pressures and temperatures.
The Rheem air-conditioner would not cool. Checked the air-conditioner and found that it was very dirty. I cleaned the air conditioner and checked all components. Found the system was short of Freon. Added 15 ounces of R-22 to bring to proper pressures and temperatures.
Performed the spring air-conditioner tuneup. Checked the thermostat and filter. Turned off the humidifier. Washed the outdoor unit. Checked all electrical connections. Checked the Freon charge. Verified the proper pressures and temperatures.
Replaced emergency disconnect box and contactor on a 2006 Tempstar air conditioner.