DeSoto Heating and Cooling
Looking to have a skilled Air Conditioning Contractor provide you with the quality services that you need to ensure that your home stay nice and cool. Our experienced staff has assisted many home owners to get the services that they desire for their homes. Whether they have a newer or older cooling systems it does not matter.
For all of your De Soto air conditioning needs give the expert staff at Ideal Air Heating & Cooling a call and see what they can do for your air conditioning needs today.
Ideal Air Heating & Cooling – De Soto Air Conditioning
De Soto Central heating and air units can provide a comfortable environment for your home when properly maintained. In homes, central A/C units provide cool air flow, directly from the source, into every room in the house. This is why over 80% of new homes built in the United States are equipped with a central A/C unit.
In the workplace and businesses, these De Soto central air conditioners, or HVACs, provide a better environment for both workers and consumers (whichever one you are being at that time). Studies show that people are more alert and more productive when in a comfortable environment. This is doubly true for temperature. People have been observed to be the most productive at 72°-74°. So give your De Soto air conditioning contractor a call and see what they can do for you today.
De Soto -Lawn Heating Contractor
Good De Soto heating systems are important to every home. Whether they have centralized heating units or just the local ones, both still calls for proper maintenance. Even if modern advances in technology have improved heating system operations nowadays, machines will remain machines, and they will always need repairs along the way. For this particular part, you are going to need professional hands to handle your heating repairs issues.
Hiring a professionals for De Soto heating repairs inside your house is always a smart move. This will both save you time and money, lots of it. If you have no prior knowledge in repairs to begin with, you will only do more to the existing damage, which then sums up to costly repairs. You wouldn’t want that, would you?
for DeSoto, KS
AC tune up and service. Richard did a great job. I will look forward to another service call from him
Sheila porter - Overland Park, KS
Richard is a very capable, bright, personable service agent. He answered our questions far better than previous agents with other companies. We woul give him a 10.
punctual, cordial, knowledgeable
Owen - Leawood, KS
Richard, the Ideal techs and office support are product knowledgeable and fair priced for their service. Ideal has installed a zone damper, York heat pump, AC/FAG system and two water heaters for me over the past couple years.
Excellent Service as always!
Google User - Shawnee, KS
Always great service!
Michelle - Overland Park, KS
We always have had excellent service from Ideal Air. I would highly recommend them!
Heater now works
Brandon - Olathe, KS
Linda - Shawnee, KS
Ideal Air Heating and Cooling are always a pleasure to deal with. They take their time and don't through a job and are always willing to answer all my questions. I feel I'm in good hands with Ideal Air Heating and Cooling and would definitely recommend them to a friend.
Excellent professional service!
Cliff - Lenexa, KS
Richard always does excellent service here. He always explains exactly what he is doing...no surprises.
Responded to a no cooling call on a 2004 Tempstar air conditioner model number NAC042AKC3. Cause of problem is the air conditioner is short of freon. Customer knows there is a leak and chooses to recharge it every year. Recharged with R-22 to proper pressures and temperatures.
Was called with a no cooling complaint and to come and do an A/C repair on a 1995 Lennox air conditioner model number 10ACB42-3P. Found the entire electrical box was burned up. System required a new contactor, capacitor, and start kit. Replaced those parts to correct. Started system and it was short of freon. Added R-22 to proper pressures.
Checked Goodman air conditioner and found it was short of freon. Performed complete service and tune up and then charged to proper pressures and temperatures.
Performed an air conditioner tune up and repair on a Lennox furnace and Grandaire air conditioning system. System had no freon. Found multiple leaks at the outdoor unit. The furnace is very old and in bad shape. The air conditioning and heating system needs to be replaced.
Air conditioner would not cool because it was short of freon. Completely checked the 2004 Carrier air conditioner. Added R-22 freon to charge to proper pressures and temperatures.
Checked on a York heat pump that was not cooling. The heat pump was very low on freon. The service caps were missing off of the heat pump. They had been missing for a long time. Seed the proper amount of R410a freon and installed new caps. Checked the heating and cooling system operation.
Performed an A/C tune up on a Bryant air conditioner system. Washed the outdoor air conditioner. Checked all of the electrical. Checked the freon charge. Checked the furnace filter.
Performed a new A/C start up on a new York air conditioner. Added a little bit of R410a freon to bring to proper pressures and temperatures.
Performed air conditioner tune ups on two systems. One of them is a York system, and the other is a Lennox. Checked freon levels and all electrical. Cleaned the air conditioners. Replaced the filters.
Performed spring air conditioner tune up on a 2003 Trane system. Checked freon levels and all electrical.
Performed spring A/C tune up of a York air conditioner. Checked all the vital functions of the system.
Performed a spring A/C tune up. Turned off the humidifier. Serviced the entire system. The Lennox HS-21 air conditioner had a bad contactor. Replaced the contactor to correct.
Checked a Lennox air conditioner because of no cooling. Discovered a grounded compressor. Air conditioner needs to be replaced.
Air conditioner was not cooling. Found that the a/c and the furnace were not running. Checked the Lennox furnace and found a bad circuit board. Replaced the circuit board to correct and checked the system operation.
Responded to a no air conditioning call. Worked on a 2004 Carrier model 38TSA042. Cause of problem was a bad dual voltage capacitor. Replaced the capacitor and checked the operation. Washed the air conditioner. System was a little short of freon. Charged to proper pressures and subcooling.
Tuned up a 2010 Goodman air conditioner.
Tune up on a 1998 Lennox air conditioner.
Tuned up a 2000 Lennox air conditioner.
Performed a spring A/C tune up. Checked freon levels for proper pressures and temperatures. Serviced the humidifier and checked the high efficiency air filter
Checked air conditioner operation. It was short of freon. I did a leak search. Located and repaired leak.
Performed spring air conditioner tune up. Checked system operation and refrigerant charge. System had correct levels of freon. No problems found.
Air conditioner was iced up. It iced up because it was short of freon. Located leak in the evaporator coil. Added R-22 to the proper pressures and temperatures.
Performed air conditioner tune up. Checked total A/C operation.
Tuned a 1985 York air conditioner. Added correct charge of refrigerant, and stated Energy Savings Agreement annual plan.
Performed spring A/C tune up. Completely checked the system. Customer started an annual maintenance agreement.